oil-fired furnaces and boilers
A number of retrofits are possible for oil-fired furnaces and boilers, but before pursuing any retrofits you should consider the potential added benefits you could receive by simply replacing the furnace. The following retrofits are possible:
Vent dampersThe most common retrofit is the addition of a vent (or flue) damper. A vent damper prevents chimney losses by closing off a boiler's vent when the boiler isn't firing. Steam boilers benefit from vent dampers more than hot-water boilers, and bigger boilers benefit more than smaller ones. Vent dampers, however, may not be cost effective with properly sized, newer furnace models. For older oil burners, converting to a flame retention burner (below) is probably a better investment.
Barometric flue damperDuring your annual service checkup, have your technician perform a draft test. If too much heat is going up the chimney, you may need to install a barometric flue damper. The cost is less than $100 and could save you about 5% of your fuel cost.
Derating or replacing oil burnersMany boilers and furnaces in today's homes are oversized, particularly if you've upgraded the energy efficiency of your home. It is simple to reduce the heating capacity of your oil boiler or furnace to make it operate more efficiently by having a technician install a smaller nozzle. The cost is minimal and it could cut fuel bills by as much as 10%.
If you have an old, inefficient burner, though, you may want to replace the whole burner. A flame retention burner will block airflow up the chimney when the unit isn't running, saving up to 20% on fuel costs at a cost of about $500. Note that steam boilers should only be derated if the steam system is also modified to remove excess radiators, which is a tricky procedure.
Modulating aquastats (for hot water boilers only)An aquastat controls the temperature of the hot water in a boiler, typically keeping it around 180°F. But when heating needs a lighter in the spring and fall, that's actually higher than needed, and wastes energy. A modulating aquastat, also called an outdoor reset, senses outdoor temperatures and adjusts the hot water temperature accordingly. The units can save up to 10% of fuel costs, and cost several hundred dollars.
A cheaper alternative is to manually adjust the aquastat yourself, turning it down to around 120°F during the milder heating season. Consult your owner's manual or a service technician to locate the aquastat.
Time-delay relay (for hot water boilers only)A time delay relay is a way to squeeze the most heat out of your system without running the boiler. When the thermostat clicks on, the relay causes the boiler to circulate hot water through the system without turning on the boiler. After a set time, the boiler will fire up. A time delay relay costs about $100 and can cut your fuel costs by up to 10%.
Related category• HEATING
Home • About • Copyright © The Worlds of David Darling • Encyclopedia of Science • Contact